Black Box Explains...DIN rail usage.
DIN rail is an industry-standard metal rail, usually installed inside an electrical enclosure, which serves as a mount for small electrical devices specially designed for use with DIN rails. These... more/see it nowdevices snap right onto the rails, sometimes requiring a set screw, and are then wired together.
Many different devices are available for mounting on DIN rails: terminal blocks, interface converters, media converter switches, repeaters, surge protectors, PLCs, fuses, or power supplies, just to name a few.
DIN rails are a space-saving way to accommodate components. And because DIN rail devices are so easy to install, replace, maintain, and inspect, this is an exceptionally convenient system that has become very popular in recent years.
A standard DIN rail is 35 mm wide with raised-lip edges, its dimensions outlined by the Deutsche Institut für Normung, a German standardization body. Rails are generally available in aluminum or steel and may be cut for installation. Depending on the requirements of the mounted components, the rail may need to be grounded. collapse
Industrial Ethernet Surge Protector DIN Rail Specification Sheet
Specification Sheet for the ICD300A
Product Data Sheets (pdf)...APC ProtectNet
Product Data Sheets (pdf)...Opto-Isolators
RS-232 Surge Protector, DB15 Manual
Manual for SP507A (Version 1)
Black Box Explains…Sizing a UPS
The power delivered by a UPS is usually expressed both in volt-amps (VA) and watts. There’s often confusion about what the difference is between these figures and how to use... more/see it nowthem to select a UPS.
VA is power voltage multiplied by amps. For instance, a device that draws 5 amps of 120-volt power has a VA of 600. Watts is a measure of the actual power used by the device. VA and watts may be the same. The formula for watts is often expressed as:
Watts = Volts x Amps
This formula would lead you to believe that a measurement of VA is equal to watts, and it’s true for DC power. AC power, however, can get complicated. Some AC devices have a VA that’s higher than watts. VA is the power a device seems to be consuming, while watts is the power it actually uses.
This requires an adjustment called a power factor, which is the ratio of watts to VA.
AC Watts = Volts x Amps x Power Factor
Watts/VA = Power Factor
Simple AC devices, such as light bulbs, typically have a power factor of 100% (which may also be expressed as 1), meaning that watts are equal to VA like they are with DC devices. Computers have had a much lower power factor, traditionally in the 60–70% range. This meant that only part of the power going into the computer was being used to do useful work.
Today, however, because of Energy Star requirements, virtually all computing devices are power factor corrected and have a power factor of more than 90%.
Which brings us around to how to use this information to select a UPS. The capacity of a UPS is defined as both VA and watts. Both should be above the power requirements of the connected equipment.
Because of the computers that had a low power factor, UPSs typically had a VA that was much higher than watts, for instance, 500 VA/300 watts. In this case, if you use the UPS with a power factor corrected device that requires 450 VA/400 watts, the UPS won’t provide enough wattage to support the device.
Although UPSs intended for enterprise use now normally have a high power factor, consumer-grade UPSs still typically have a lower power factor—sometimes even under 60%. When using these UPSs, size them by watts, not VA, to ensure that they can support connected equipment.
Product Data Sheets (pdf)...Elite Managed Power Controllers
Product Data Sheets (pdf)...Network Power Switch Jr.
Metered Rackmount PDU with Front and Rear Outlets, 15-Amp