Product Data Sheets (pdf)...Wallmount Equipment Termination Cabinets
- Visio Stencil Drawing...
Product Data Sheets (pdf)...NetRack
Find the right screw length for your cabinet or rack.
Types of Screws
There are two basic kinds of screws used for cabinets and racks—panhead screws and countersunk screws—and... more/see it nowthey’re measured in two different ways. Because the standard way to measure is from the tip of the business end of the screw to where the screw rests on the material it’s fastened to, a panhead screw is measured to the bottom of its head, whereas a countersunk screw is measured to the top of its head.
Elite Wallmount Cabinet User Manual
Black Box Explains...Cable management.
Product Data Sheets (pdf)...Performance Plus Cabinets
Corporate networks are complex systems of PCs, servers, printers, and the devices that connect them. Getting everything to work in harmony requires bundles of cables, and managing all those cables... more/see it nowfrom inside a telecommunications closet can be a daunting task. To connect cable bundles to rackmounted equipment (like patch panels, hubs, switches, or routers), you need to direct the bundles overhead, vertically, and horizontally.
A popular choice for overhead cable routing is a ladder rack. Ladder racks come in many varieties. They can run along a wall supported by brackets or they can be installed overhead and supported by a threaded rod. Ladder racks can support large cable bundles neatly and safely. Because bundles lie flat on a ladder rack, cables aren’t subjected to harsh bends. You can run ladder racks directly to the top of most standard telecommunications racks that conform to TIA/EIA standards.
Use vertical cable managers to route cable bundles along the sides of a rack. These “cable troughs” as they’re sometimes called can be single sided—or double sided to route cable bundles to the rear of equipment and to the ports on the front as well. Vertical cable managers usually come with some type of protection for the cable, such as grommeted holes to protect the cable jacket or a cover that may clip on or act as a door.
Horizontal cable managers are usually a series of rings that directs cables in an orderly fashion toward the ports of hubs, switches, and patch panels. collapse
Black Box Explains...10-32, 12-24, and M6 rails.
Product Data Sheets (pdf)...23"-to-19" Rackmount Adapters
The rails on cabinets and racks typically come with one of three mounting options: 10-32, 12-24, or M6.
The 10-32 and 12-24 options are round holes found on drilled and tapped... more/see it nowrails. You’ll find 10-32 openings on cabinets, while 12-24 holes are more commonly found on relay racks and frames. However, exceptions do exist. It’s very important to find out which type of mounting option your equipment requires before you order a cabinet or rack.
M6 holes are square, rather than round. M6 rails were developed to hold rackmount equipment, and you will find them on most server cabinets.
What makes M6 rails so popular on server cabinets? They’re adaptable. With just one cage nut, you can change a square hole into a round one. That gives you much more versatility in your equipment and mounting choices.
If you have a wide array of equipment, such as rackmount servers, hubs, routers, and patch panels, your best bet is a cabinet with M6 rails. It will accommodate the rackmount servers, and the other equipment can be mounted on those same rails using cage nuts.
If you’re unsure what type of cabinet, rack, or frame is best for your application, contact the experts at Black Box Tech Support. They’ll be glad to help you find the right enclosure for your equipment. collapse