Product Data Sheets (pdf)...Fan Thermostat Controller
- Visio Stencil Drawing...
Comm Cabinets and Accessories
Users Manual (Jul-03)
Black Box Explains…How to keep cabinets cool.
Product Data Sheets (pdf)...Universal Server Cabinets
Product Data Sheets (pdf)...Pro Series Wallmount Cabinet
Product Data Sheets (pdf)...Quiet Fan Panels
Networking equipment—especially servers—generates a lot of heat in a relatively small area. Today’s servers are smaller and have faster CPUs than ever. Because most of the power used by these... more/see it nowdevices is dissipated into the air as heat, they can really strain the cooling capacity of your data center. The components housed in a medium-sized data center can easily generate enough heat to heat a house in the dead of winter!
So cool you must, because when network components become hot, they're prone to failure and a shortened lifespan.
Damage caused by heat is not always immediately evident as a catastrophic meltdown—signs of heat damage include node crashes and hardware failures that can happen over a period of weeks or even months, leading to chronic downtime.
Computer rooms generally have special equipment such as high-capacity air conditioning and raised-floor cooling systems to meet their high cooling requirements. However, it's also important to ensure that individual cabinets used for network equipment provide adequate ventilation. Even if your data center is cool, the inside of a cabinet may overheat if air distribution is inadequate. Just cranking up the air conditioning is not the solution.
The temperature inside a cabinet is affected by many variables, including door perforations, cabinet size, and the types of components housed within the cabinet.
The most direct way to cool network equipment is to ensure adequate airflow. The goal is to ensure that every server, every router, every switch has the necessary amount of air no matter how high or low it is in the cabinet.
It takes a certain volume of air to cool a device to within its ideal temperature range. Equipment manufacturers provide very little guidance about how to do this; however, there are some very basic methods you can use to maximize the ventilation within your cabinets.
Open it up.
Most major server manufacturers recommend that the front and back cabinet doors have at least 63% open area for airflow. You can achieve this by either removing cabinet doors altogether or by buying cabinets that have perforated doors.
Because most servers, as well as other network devices, are equipped with internal fans, open or perforated doors may be the only ventilation you need as long as your data center has enough air conditioning to dissipate the heat load.
You may also want to choose cabinets with side panels to keep the air within each cabinet from mixing with hot air from an adjacent cabinet.
Don't overload the cabinet by trying to fit in too many servers—75% to 80% of capacity is about right. Leave at least 1U of space between rows of servers for front-to-back ventilation. Maintain at least a 1.5" clearance between equipment and the front and back of the cabinet. And finally, ensure all unused rack space is closed off with blank panels to prevent recirculation of warm air.
Fans and fan placement.
You can increase ventilation even more by installing fans to actively circulate air through cabinets. The most common cabinet fans are top-mounted fan panels that pull air from the bottom of the cabinet or through the doors. For spot cooling, use a fan or fan panel that mounts inside the cabinet.
For very tightly-packed cabinets, choose an enclosure blower—a specialized high-speed fan that mounts in the bottom of the cabinet to pull a column of cool air from the floor across the front of your servers or other equipment. An enclosure blower requires a solid or partially vented front door with adequate space—usually at least 4 inches—between the front of your equipment and the cabinet door for air movement.
When using fans to cool a cabinet, keep in mind that cooling the outside of a component doesn't necessarily cool its inside. The idea is to be sure that the air circulates where your equipment's air intake is. Also, beware of installing fans within the cabinets that work against the small fans in your equipment and overwhelm them.
To ensure that your components are operating within their approved temperature range, it’s important to monitor conditions within your cabinets.
The most direct method to monitor cabinet temperature is to put a thermometer into your cabinet and check it regularly. This simple and inexpensive method can work well for for small installations, but it does have its drawbacks—a cabinet thermometer can’t tell you what the temperature inside individual components is, it can’t raise the alarm if the temperature goes out of range, and it must be checked manually.
Another simple and inexpensive addition to a cabinet is a thermostat that automatically turns on a fan when the cabinet's temperature exceeds a predetermined limit.
Many network devices come with SNMP or IP-addressable internal temperature sensors to tell you what the internal temperature of the component is. This is the preferred temperature monitoring method because these sensors are inside your components where the temperature really counts. Plus you can monitor them from your desktop—they’ll send you an alert if there’s a problem.
There are also cabinet temperature sensors that can alert you over your network. These sensors are often built into another device such as a PDA but only monitor cabinet temperature, not the temperature inside individual devices. However, these sensors can be a valuable addition to your cooling plan, especially for older devices that don't have internal sensors.
The future of cabinet cooling.
Very high-density data centers filled with blade servers present an extreme cooling challenge, causing some IT managers to resort to liquid-cooled cabinets. They’re still fairly new and tend to make IT managers nervous at the prospect of liquids near electronics, but their high efficiency makes it likely that these liquid-cooled systems will become more prevalent.
It’s easy, really.
Keeping your data and server cabinets cool doesn't have to be complicated. Just remember not to overcrowd the cabinets, be sure to provide adequate ventilation, and always monitor conditions within your cabinets.
Black Box Explains…Liquid cooling.
The trend toward high-density installations with higher-powered CPUs has made heat a critical issue in data centers. Blade servers present a special challenge—a rack of blade servers can dissipate more... more/see it nowthan 25 kW, generating more heat than an electric oven.
The heat generated in today’s high-density data centers can shorten equipment lifespan, negatively affect equipment performance, and cause downtime.
Traditional air-cooling methods such as hot/cold aisle arrangements simply can’t keep up with these heat-generating installations. Data center managers often try to compensate for the inefficiency of air cooling by under-populating racks, but this wastes space—an often scarce commodity in modern data centers.
Because of the inherent inefficiencies of air cooling, many data centers have turned to liquid cooling through water or other refrigerants. Liquids have far greater heat transfer properties than air—water is 3400 times more efficient than air—and can cool far greater equipment densities.
Liquid cooling is usually done at the rack level using the airflow from the servers to move the heat to a cooling unit where it’s removed by liquid, neutralizing heat at the source before it enters the room. Liquid cooling may also be done at the component level, where cooling liquid is delivered directly to individual components. Liquid cooling may also arrive in the form of portable units for cooling hot spots.
Liquid cooling options
Types of liquid cooling commonly used in data centers include:
- Cabinet-door liquid cooling: With this method, cooling units are special cabinet doors that contain sealed tubes filled with chilled liquid. The liquid is circulated through the door to remove heat vented by equipment fans. Because liquid-cooled doors can replace standard cabinet doors, they’re the favored method for retrofitting liquid cooling into existing data centers.
- Integrated liquid cooling: This consists of a specialized sealed cabinet that has channels for liquid cooling built into it to act as heat exchangers. Fans move hot air past the heat exchangers before sending the cooled air back to the servers. These cabinets are closed systems that release very little heat into the room.
- Component-based liquid cooling: Some servers are preconfigured with integrated liquid-based cooling modules. After the servers are installed, liquid is circulated through the cooling modules.
- Immersion cooling: This rather counterintuitive cooling method immerses servers in a non-conductive liquid, which is circulated to cool the servers.
- Portable liquid cooling: These are small units that operate by blowing air across water-cooled coils. They can usually accept water from any source—including a nearby faucet. They’re generally plumbed with ordinary garden hoses and require no special skills to use. Portable cooling units are intended for emergency cooling rather than as a permanent solution.
Liquid cooling requires a shift in the way you think about cooling. Installation may require that you acquire a new skill set or hire a professional installer. However, the space savings and cost savings gained through liquid cooling more than make up for the inconvenience of installing a new cooling technology.
Not only does liquid cooling enable data centers to operate at far greater densities than conventional air cooling does, it gets rid of the infrastructure associated with air cooling, enabling you to eliminate hot/cold aisles and raised floors. Liquid cooling can support from 25 to 80% more equipment in the same footprint, resulting in significantly lower infrastructure costs.
Add to this the fact that cooling is often the majority of a data center’s operating cost, and it’s plain to see why an investment in the efficiency of liquid cooling goes right to the bottom line.
Product Data Sheets (pdf)...Cold Front
Pro Series Wallmount Cabinet User Manual
User Manual for the RM4001A. RM4002A, RM4003A, RM4004A, RM4005A, & RM4007A (Version 1)